Fixing Error Code 228 on Your Lennox® Furnace
Not sensing any heat and receiving error code 228 from your Lennox® furnace?
This indicates your furnace couldn’t correct its pressure switch before turning on. As a consequence, your system will not run for your safety.
Repairing or replacing this part is better left to the Experts at Atmostemp Service Experts in Voorhees. Our ACE-certified technicians are among the best in the industry. They’re well-qualified to work on all of your heating needs, including fixing a furnace error.
We want you to be absolutely satisfied with our quality furnace repair* for a year.
How a Pressure Switch Works
This part plays a critical duty as your furnace prepares to work in your house.
Here’s what goes on after your thermostat’s call for heat:
- Your furnace’s control board commences running the draft inducer blower motor. This drains combustion gases from the heat exchanger and pulls in new gas and air so the burners can fire.
- When the pressure switch senses that enough air is being pulled into the burners, it closes and signals the control board to ignite the furnace.
- Your furnace ignites and provides heat.
What Happens When a Pressure Switch Fails
When your pressure switch isn’t working correctly, you’ll likely hear the fan going and the switch clicking a few times before the furnace switches off completely. When a part isn’t functioning right, your furnace will turn off to protect you.
Your furnace will let you know something is incorrect with a red flash from its indicator light, which it uses to present error codes. It uses this red light to flash code, like Morse code.
You may note fast flashes or an alternating slow flash as it transmits a fault code.
Estimated Repair Cost for Furnace Error Code 228
Before replacing the switch, your Atmostemp Service Experts tech will investigate other parts of your furnace first. A handful of other issues can also generate the error code, like a clogged vent or cracked hose.
The price to repair your furnace depends on the issue with it and how long it takes to fix it.
If your pressure switch needs to be replaced, you can anticipate to pay between $40 to $350.
Start with the Experts at Atmostemp Service Experts
If you should have furnace repair, reach out to the pros from Atmostemp Service Experts to diagnose the fault code and fix the situation to your standards.
Call us at 856-310-4824 or schedule an appointment online today.